Transactions of the Japan Society of Mechanica
Usually, we operate hand firing steam boiler in the state of damper opening constant, and stoke at certain interval. And then, excess air factor is changed between certain consecutive stokings. On the contrary, on most chain grate stoker boiler, for each fuel consumption, excess air factor, which give a maximum efficiency curve are decided.
Get A Quote >